This job in Jericho involved repairs to the service equipment due to an electrical fire.
We installed a new 3 gang meter socket with (3) 200 amp raintight main circuit breakers.
We megohm meter tested the PSEG underground feeders to the property box and reconnected them to the new equipment.
We megohm meter tested the 200 amp feeders from the service to the 200 amp panels in each home.
The service conductors were cut back and rewired from junction boxes in an accessible area to the new main disconnects.
We obtained a temporary certificate of approval and made arrangements for a quick PSEG reconnect to restore power so that the owners could return to their home.
We obtained a final certificate of approval from the electrical inspectors that verified all of the repairs complied with the rules and regulations of the National Electrical Code.